Here is an example of testing exterior Radio and Microwave (RF/MW) and Magnetic Field levels. Be sure to test every home before buying! We can fix most any problem inside the home. These exterior influences are deal breakers from the start.
This shows how a parallel neutral creates a magnetic field. Unfortunately, bundling neutrals from different circuits is a very common electrical practice and needs to be sorted out. Don't add any dirty electricity filters until you have had your neutrals checked. The dirty electricity will be broadcast throughout that magnetic field!
This just scratches the surface on the Neutral Check (parallel neutrals) and problems caused by neutral/ground connections.
The overwhelming majority of homes have current coming into their Service cabinets from their Cable TV/Internet line. Fortunately, there is a very easy and inexpensive way to stop it.
It is critically important to remove any current from the water pipes before it comes into your house or panel. See the resulting magnetic fields, body voltage and contact current levels in this video.
Since 1996, the National Electrical Code (NEC) requires 120/240V cooktop/ranges, dryers and other such appliances to have 4 wires. Here is the problem with using only 3. Notice the body voltage and contact current levels.
Unfortunately, this is a big problem with many Ranges and Dryers in homes since 1996. Many STILL come from the factory with their neutral and ground connected! Have you checked yours?
Here are two quick examples of how a neutral to ground connection can be made, one through a burned lamp fixture and the other through a dryer. This effects the whole house as all the neutrals and grounds will have continuity.
Here is a good way to use Greenwave or Stetzer filters at the panel, with dedicated A and B phase outlets. Using the PxDNA filters are best if you can afford them.
Turning off multiple breakers at once AND cutting the neutrals and hots at the same time with a contactor box is shown here.
There are are UL approved whole house EMF reducers available.
See a ground wire touching the neutral inside an outlet. The neutral wire was open, disconnected, but the light was still working, using the ground for the return pathway. Current was being added to the grounds throughout the house! Not good.
Turning off the breakers at night is one of the best and easiest ways to lower body voltage, eliminate dirty electricity and remove some magnetic fields.
Always check with a body voltage meter the true effect of throwing on/off breakers. Just turning off your bedroom breaker does not guarantee lower body voltage. In fact, sometimes, it makes it worse.
There are also options to make this more convenient than having to go to the panel each night, like installing double pole outlet switches.
This demonstrates how much current and body voltage (electric field) emits off of an ungrounded lamp. It actually radiates through the air from a fluorescent bulb! Fortunately this is easy to fix with a 3 wire shielded/grounded cable and using incandescent bulbs.
Here is an easy way to check if there is current on your equipment grounding conductor which represents incorrectly wired appliances, circuits, junction boxes and other code violations.
The Radon vacuum pump was installed incorrectly and put current onto the grounds in the home.
I have found that we won't be able to achieve 50mV or lower body voltage for good sleeping unless we separate the grounds and neutrals in the distribution/breaker panel. See this engineer's explanation: http://www.esgroundingsolutions.com/why-separate-the-ground-bar-from-the-neutral-bar-in-a-sub-panel/
After you have found current on the grounding conductor, here is how you fix it. This is one of my most important procedures to find and fix, arguably, the worst electrical problems in a home.
The continuity check procedure between the neutrals and grounds in the distribution panel is a great way to find improperly wired appliances, junction boxes, outlets, anywhere a neutral will conduct current to a grounding electrode conductor.
Great for finding the NEC 250.6 (A) Objectionable Current.
This office building had an extra bond between Services which created a ground loop. A magnetic field was created inside the offices.
There is a lot in this video if you want to dive deep.
Everything published on this website is for informational purposes only. It is not intended to be or replace medical advice offered by physicians or any other licensed health care provider. This site, its authors or associated participants will not be liable for any direct, indirect, consequential, special, exemplary, or other damages arising from information obtained from this website.
Copyright © 2018 Home EMF Tracing